LOVATO ELECTRIC DCRK7 | Module: reactive power controller; Outputs:7; ÷ 60°C – This product is available in Transfer Multisort Elektronik. Check out our. DCRK7 by Lovato | LOVATO AUTO POWER FACTOR CONTROLLER 7 STEPS VAC 96 X 96MM | Shipping to + countries worldwide. Buy DCRK7 LOVATO ELECTRIC POWER FACTOR CONTROLLER DCRK7 INPUT /VAC the best price, fast worldwide shipping, up to 65% discount.
|Published (Last):||21 May 2011|
|PDF File Size:||4.43 Mb|
|ePub File Size:||7.78 Mb|
|Price:||Free* [*Free Regsitration Required]|
We think you have liked this presentation. If you wish to download it, please recommend it to your friends in any social system.
Share buttons are a little bit lower. Published by Mark Adams Modified over 3 years ago. DCRK regulators can read correctly the D. In a system without harmonics, the power factor dccrk7 the same value as COSj.
In other conditions, the power factor is less than the COSj. Power factor correction systems can adjust the COSj to the required value and can thereby obtain the best possible lovat factor. It is calculated in the same way used by energy suppliers, storing active and reactive energy meters in DCRK internal memory.
This value is therefore a true efficiency index of the entire reactive power correction system.
This avoids inverting the CT connections during installation. In cogeneration plants, where it is necessary to operate in 4-quadrant, the CT connection sense must be set manually. The adjustment is conducted dcr7k a precise manner and not by consecutive attempts. The reduction of the number of operations substantially lowers the capacitor and contactor wear. The uniform operation of the steps prolongs the life and efficiency of both the capacitors and contactors.
In case of step wear, all the relative power parameters are automatically recalculated. This allows the DCRK unit to work rapidly and efficiently, that is with fewer and lpvato operations. The voltage waveform is analysed by special algorithm that calculates the exact percentage of the current flowing in the capacitors.
AUTOMATIC POWER FACTOR CONTROLLER, DCRK SERIES, 7 STEPS | Lovato Electric
Once lovayo set current overload threshold limit is exceeded, the capacitors are disconnected within a time inversely proportional to the exceeding limit. THD Total Harmonic Distortion does not change with harmonic dcr7k, and therefore it is not an indicator of capacitor overload. This temperature value is displayed and the maximum value is logged. By setting related parameters, a threshold can be set to switch on a relay to operate a ventilation system.
It is also possible to set an higher threshold to generate an overtemperature alarm. When working with cogeneration plants, automatic CT connection feature cannot be used.
In this case, during the system installation and once the controller is powered up, the display will show a drck7 CT indicating that the CT has not been programmed. Just selecting the correct value from the list and storing it with one key will enable the DCRK operation.
Just pushing two keys, the user is able to put the DCRK into operation.
Lovato DCRK7 – POWER FACTOR CONTROLLER 7 STEP /
Once programmed, the following operations will be locked: The DCRK programmed parameters can also be stored on the PC and quickly downloaded into an unlimited number of units, which require the same programming. The customising of alarm properties can be made as well as the automatic panel testing with the control of the power installed and the test report printing too.
Counter for the number of switching operations of each capacitor kovato. Time counter for the total connection time of each capacitor step. Installation base of over 25, valued installations, Country wide Installation base of over 25, valued installations, Country wide Recognised as. FP Refer to for the latest information on this constantly evolving productwww. My presentations Profile Feedback Log out.
Auth with social network: Registration Forgot your password? About project SlidePlayer Terms of Service.
DCRK DIGITAL POWER FACTOR CONTROLLERS